If the panel is not configured sims for stand-alone operation, the amplifier will not output any signal.
The largest, the 3-CAB21 supports as many as 18 rail modules and 19 control/display modules.EST3 Smoke Management Application Manual (P/N Provides information for designing, word programming, and testing an EST3 program smoke control system.When an alarm is detected, the evacuation and alert message channels are selected by the amplifiers in program the appropriate areas in the facility, as directed by the system rules.SDU Online Help (P/N Provides full online support for configuring and programming a system using the System crack Definition Utility program.The customer should be aware that compliance with the above conditions may not prevent degradation of service in some situations.EST3 Installation and Service Manual v 8 Content Repairs to certified equipment should be made by an authorized Canadian maintenance facility designated by the supplier.Figure 1-11 shows the wiring for a Class A network.The evac and alert channels are connected to their respective signal sources, as in the normal mode.Vi EST3 Installation and Service Manual 9 UL 864 9th break edition requirements notice TO users, installers, authorities having jurisdiction, AND other involved parties This product incorporates field-programmable software.Figure 1-8 shows the all call minus mode page source to auxiliary and general channel connections.Most field wiring is terminated using removable terminal strips for easy installation and servicing of modules.Figure 1-9: Automatic Message sims game Processing The generic (default) evacuation message plays when multiple location specific messages have been requested by the system or when no location specific message has been specified.Primary Power Supply module (3-PPS/M, 3-BPS/M, or 3-BBC/M) one required for each panel) 3-LCD(XL) Display module Control/display modules as required 3-BPS/M Booster Power Supply module 3-modcom Modem Communicator module 3-SAC Security Access Control module 3-ssdc1 and 3-sddc1 Signature Driver Controller module 3-aadc1 Analog Addressable Driver.EST3 Installation and Service Manual.7 22 System overview smoke Network Data Riser Network Audio Riser Equipment Enclosure word Central Processor Module Local Rail Bus Backup Amplifier Zoned Amplifier Zoned Amplifier Zoned Amplifier Zoned Amplifier amplifier_R Page Page evac Alert Figure 1-4: Normal amplifier operation Possible fault.In firex this mode, the zoned audio amplifiers do not all transfer to the page channel.Connect here to download data to all three programmable rail modules over the rail bus (network mode) or to this programmable rail module only (single-step furious mode) K 1 K 1 output module output module S 2 S 2 R Optional serial ports may be used.Windows code page Languages supported 1250 (Eastern Europe) English, Polish Slovak 1251 (Cyrillic) English, Russian 1252 (Western Europe) Dutch, gauge English, French, Italian, Portuguese, Spanish 1254 (Turkish) English, Turkish 1255 (Hebrew) English, Hebrew.22 EST3 Installation and Service Manual 37 System overview Example: Bilingual operation between.3 Content Important information v UL 864 9th edition requirements vii About game this manual x The EST3 library xii Related documentation xiii Chapter game 1 System overview.1 System description.2 Audio subsystem description.6 Digital network subsystem.16 Foreign language support.22 Signature series devices.The evac, auxiliary and general channels are connected to their respective signal sources, as in the normal mode. 21OCT Incorporated changes concurrent with software release version.5.
(Y/N) ossible est3 installation and service manual settings No Yes No Yes Y Disabled (0) 1 second to 99 hours AC Power Delay Y Disabled 1 minute to 45 hours Event message routing Y All Cabinets No Cabinets User defined routes (1 to 15) Event message display filtering: Alarm, Supervisory.
An independent supervised Class B or Class A, 24 Vdc,.5 Amp notification appliance circuit (NAC) is also provided on the 20- and 40-watt amplifiers to drive notification appliances.
Amplifier switches to the evac or alert channel only in response to the local panel s programming uses the default evac message.